Electronics Forums > 3 phase power formula

# 3 phase power formula

Guest
Posts: n/a

 02-25-2004, 01:16 AM
the three phase power formula goes like this:

V * I * 1.732 * PF

where V - voltage, I - current, PF - power factor

a 3 phase generator set to 120/208 V with amperage values of 24A, 26A, 22A
at each phase.. PF is 0.8

which V value should i use? do i take the average current (I) or do i add
them up?

John Popelish
Guest
Posts: n/a

 02-25-2004, 01:29 AM
>
> the three phase power formula goes like this:
>
> V * I * 1.732 * PF
>
> where V - voltage, I - current, PF - power factor
>
> a 3 phase generator set to 120/208 V with amperage values of 24A, 26A, 22A
> at each phase.. PF is 0.8
>
> which V value should i use? do i take the average current (I) or do i add
> them up?

If the three currents listed are the 3 line to neutral currents (not
line to line current) then you just use the single phase formula 3
times and add the results. 120V*A*PF

--
John Popelish

Lord Erdel
Guest
Posts: n/a

 02-25-2004, 01:46 AM
which brings me to another question.. what am i measuring when i use a
clamp-on ammeter? am i correct in stating this equation then?

P = V[phase-ground] * ( I[phase1] + I[phase2] + I[phase3]) * PF * 1.732

assuming i have the same phase voltages across the board of course..

> If the three currents listed are the 3 line to neutral currents (not
> line to line current) then you just use the single phase formula 3
> times and add the results. 120V*A*PF
>
> --
> John Popelish

Don Kelly
Guest
Posts: n/a

 02-25-2004, 05:55 AM

"erthlink" <(E-Mail Removed)> wrote in message
> the three phase power formula goes like this:
>
> V * I * 1.732 * PF
>
> where V - voltage, I - current, PF - power factor
>
> a 3 phase generator set to 120/208 V with amperage values of 24A, 26A, 22A
> at each phase.. PF is 0.8
>
> which V value should i use? do i take the average current (I) or do i add
> them up?
>

If the currents are the same in all 3 phases then use the line to line
voltage (208V). Otherwise use 120*I*pf 3 times and add them up as John has
indicated. Actually using 208*1.732*24A*pf will probalby be close enough for
government work.

--
Don Kelly
(E-Mail Removed)

phil-news-nospam@ipal.net
Guest
Posts: n/a

 02-25-2004, 05:03 PM
On Wed, 25 Feb 2004 01:16:19 GMT erthlink <(E-Mail Removed)> wrote:

| the three phase power formula goes like this:
|
| V * I * 1.732 * PF
|
| where V - voltage, I - current, PF - power factor
|
| a 3 phase generator set to 120/208 V with amperage values of 24A, 26A, 22A
| at each phase.. PF is 0.8
|
| which V value should i use? do i take the average current (I) or do i add
| them up?

Is that 0.8 PF the rating of the generator, or the actual load?

--
-----------------------------------------------------------------------------
| Phil Howard KA9WGN | http://linuxhomepage.com/ http://ham.org/ |
| (first name) at ipal.net | http://phil.ipal.org/ http://ka9wgn.ham.org/ |
-----------------------------------------------------------------------------

Lord Erdel
Guest
Posts: n/a

 02-25-2004, 11:31 PM

> Is that 0.8 PF the rating of the generator, or the actual load?
>

0.8 is my arbitrary value for PF..

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are On Pingbacks are On Refbacks are Off Forum Rules

 Similar Threads Thread Thread Starter Forum Replies Last Post bob@coolgroups.com Misc Electronics 1 01-23-2007 06:38 AM ITSME.ULTIMATE Electronic Basics 6 02-20-2006 01:20 AM Lord Erdel Electronic Basics 1 02-25-2004 03:09 AM Takoma Park Volunteer Fire Department Postmaster Electrical Engineering 9 01-29-2004 04:49 PM Carlos Electronic Design 3 12-09-2003 02:42 PM